The aerial bundled cables designed for overhead distribution lines have all conductors made of aluminium 1350 and insulated with XLPE. Phase and neutral cores are laid up in a bundle with a left hand lay. Can be used for fixed installation as overhead power lines up to 1000 V incl.
1.Phase Conductor:The conductors shall be of aluminium 1350 wires and are compacted circular stranded(RM).
2. Insulation:XLPE. 1, 2 and 3 raised longitudinal ribs on the surface of the cores. The surface of the neutral core should have at least 12 ribs for cross-sections up to 50 mm^2 and a minimum of 16 ribs for cores above 50 mm^2. In the case of five core bundles the surface of the protective core should be smooth.
3. Assembly:2 up to 4 cores of equal cross section are stranded together in left-hand lay, additionally 1 or 2 cores of reduced cross section can be co-stranded.
Aerial Bundle Cable BS7870-5 Specifications:
Get all the answers to the most frequently asked questions (FAQs) regarding Aerial Bundle Cable BS7870 chart,Aerial Bundle Cable BS7870 sizes,Aerial Bundle Cable BS7870 full form,Aerial Bundle Cable BS7870 ampacity,Aerial Bundle Cable BS7870 diameter,Aerial Bundle Cable BS7870 manufacturers and much, much more.
Aerial Bundle Cable manufactured by GE Cable meets or exceeds the requirements of all international standards like ASTM, AS, BS, CSA, DIN, IEC, NFC, SS -etc