Flexible Copper 4 Core XLPE Cable , XLPE Insulated Power Cable Low Voltage
Flexible Copper 4 Core XLPE Cable , XLPE Insulated Power Cable Low Voltage image
Brand Name :
Place of Origin :
$0.29/M ~ $120/M
Payment Terms :
Supply Ability :
20,000 Kilometers per Month
Delivery Time :
Packaging Details :
Product name :
XLPE Insulated Cable
1.0 to 630 sqmm
Free sample :
Flexible Copper XLPE Insulated Power Cable 4 Cores Low Voltage Cable
XLPE, Cross-linked polyethylene, has stable intermolecular bonds between polyethylene particles created by thermochemical action, due to the presence of organic peroxide.
XLPE has the same electricl properties as the conventional polyethylene and as result of stable intermolecular bonds, has much better thermal and mechanical properties. This provides XLPE insulated cables to be used at maximum continuous conductor temperature of 90°C while conventional polyethylene insulated cables to be used at that of 75°C. Maximum overload conductor operating temperature is 130°C ( operating at the emergency overload temperature shall not exceed 100 hours per year). Maximum conductor short-circuit temperature is 250°C. This provides an important advantage in cable ratings and is of special significance in countries or situations where the ambient temperature is high and derating factors have to be applied.
Physical and Electrical Characteristics
|Sheath||Outer Ø||weight||Current ratings in air 30℃||Current ratings buried 20℃|
|mm²||mm||mm||mm||mm||kg / km||A||A|
XLPE/PVC insulated electrical wire are covering series of wire products, and its working temperature isdifferent according to different insulation materials, mainly 70 and 90 degrees temperature, etc.
According to the conductor type, including solid conductor PVC/XL .PE insulated electrical wire,standed PVC/XL PE insulated wire, Flexible PVC/XLPE insulated wire with different colors.
According to its shape, including flat wire, round wire, etc. with different colors.
Accoding to its core number, including single core wire, multi-core wire, etc. with different colors.
The highest allowed operating temperature of conductor for long-term working is 90oC. In short-circuit(Max. Long-term is no more than 5 seconds). The highest temperature for conductor is no more than250.
D.C Resistance of the conductor complies with the stipulations of GB/T3956-1997.
The environment temperature should be no lower than 0 when lay. Otherwise it should be preheated.The cable is laid without horizontal drop limit. The Min. Bending radius of three core cable should be nosmaller than 12 times of cable outer diameter.
Partial Discharge Test: The discharge volume should be no more than 10pC under 1.73Uo for the cable.
RECOMMENDED ORDERING PARAMETERS
For prompt quotation / supplies please make sure your inquiries and your orders are securing the following data :
1 International or Special Standard. (Alternatively, the precise usage of the cable.)
2 Rated voltage.
3 Copper or Aluminium conductors.
4 Size of each conductor.
5 Insulation material : PVC XLPE or others.
6 Number and identification of conductors.
7 Other requirements.
9 Required delivery time.
10 Required validity.
If this all seems a litle too technical for you, then why not get in touch with us.We look forward to assisting you in identifying the best products for your specific application and to answer any questions you might have.
We are a manufacture in this filed for many years, we can offer our customers cables with good quality and price.
We Sincerely welcome customers at home and abroad to negotiate and cooperate with us !!!
We are China Flexible Copper 4 Core XLPE Cable , XLPE Insulated Power Cable Low Voltage manufacture and supplier,You can get more details with Email,you will get cheap price or factory price.Tags: cross linked polyethylene cable, xlpe insulated cable, xlpe power cable