STA 4 Aluminum Core NA2XBY Underground Electrical Cable Customized
STA 4 Aluminum Core NA2XBY Underground Electrical Cable Customized image
Brand Name :
Place of Origin :
Payment Terms :
T/T, L/C, Western Union
Supply Ability :
1000 km per month
Delivery Time :
Packaging Details :
standard export packing in wooden drums or boxes
Model Number :
Product Name :
4 Core STA NA2XY Underground Electrical Cable
Insulation material :
4 Core Aluminum Core STA NA2XBY Customized Underground Electrical Cable
The highest rated working temperature of NA2XBY underground electrical cable conductor is 90℃, and the highest working temperature is less than or equal to +70℃. The cable temperature within 5 seconds of short-circuit time shall not exceed 160℃, and the ambient temperature during laying shall not be lower than 0℃.
NA2XBY cables are laid indoors, in channels and pipes, and can also be buried in loose soil with insulated PVC sheathed power cables, and cannot withstand external forces. When the NA2XBY cable is laid underground, it can withstand external mechanical forces, but cannot withstand large tensile forces.
|Product name||Underground Electrical Cable|
|Rated Voltage||0.6/1 KV|
|Armoured Material||None/Steel Tape/Steel wire|
|Number of cores||1C,2C,3C,4C,5C,3+1C,3+2C,4+1C|
|Section area||1.5MM2 – 400MM2|
During the storage of the cable, the packaging should be standardized to avoid long-term open-air sun exposure, and the two ends should be reliably sealed. Long-term storage in a humid environment is not allowed, and the cable reel cannot be placed flat. The height of the tray should be considered and effectively fixed during transportation. Several trays are not allowed to be hoisted at the same time during hoisting, and it is strictly forbidden to push down from a high place.
Special tools should be used for cable laying, such as pay-off racks, guide rollers, etc., to prevent mechanical damage during the laying process and keep away from heat sources. When laying the cable through the pipe, the inner diameter of the pipe should not be less than 1.5 times the outer diameter of the cable. When multiple cables pass through the pipe, it is forbidden to squeeze the cable. The total area of the cable should not exceed 40% of the total area in the pipe.
1. Strictly implement the quality management system, the products conform to the relevant national standards and customer requirements.
2. The products are packed and transported in strict accordance with customer requirements and regulations to ensure the safety and reliability of the products during loading and unloading and transportation.
3. Product per circle of meters, less 1 meter our company add 10 meters.
4. Product implementation of three packages (quality, quantity, price), free technical advice and related technical information for customers.
5. Strict quality control on the procurement of raw materials, product production process quality control points, semi-finished products, finished products, packaging, etc., to ensure excellent product quality and timely delivery.
Underground Electrical Cable
We are China STA 4 Aluminum Core NA2XBY Underground Electrical Cable Customized manufacture and supplier,You can get more details with Email,you will get cheap price or factory price.Tags: NA2XBY Underground Electrical Cable, STA 4 Aluminum Core NA2XBY cable, STA Underground Electrical Cable, Underground Electrical Cable